<?php



if ($device['os'] == 'akcp' || $device['os'] == 'minkelsrms')
{
  $oids = snmp_walk($device, ".1.3.6.1.4.1.3854.1.2.2.1.16.1.4", "-Osqn", "");
  if ($debug) { echo($oids."\n"); }
  $oids = trim($oids);
  if ($oids) echo("AKCP ");
  foreach (explode("\n", $oids) as $data)
  {
    $data = trim($data);
    if ($data)
    {
      list($oid,$status) = explode(" ", $data,2);
      if ($status == 2) # 2 = normal, 0 = not connected
      {
        $split_oid = explode('.',$oid);
        $index = $split_oid[count($split_oid)-1];
        $descr_oid = ".1.3.6.1.4.1.3854.1.2.2.1.17.1.1.$index";
        $oid = ".1.3.6.1.4.1.3854.1.2.2.1.17.1.3.$index";
        $warnlimit_oid = ".1.3.6.1.4.1.3854.1.2.2.1.17.1.7.$index";
        $limit_oid = ".1.3.6.1.4.1.3854.1.2.2.1.17.1.8.$index";
        $warnlowlimit_oid = ".1.3.6.1.4.1.3854.1.2.2.1.17.1.9.$index";
        $lowlimit_oid = ".1.3.6.1.4.1.3854.1.2.2.1.17.1.10.$index";

        $descr = trim(snmp_get($device, $descr_oid, "-Oqv", ""),'"');
        $humidity = snmp_get($device, $oid, "-Oqv", "");
        $warnlimit = snmp_get($device, $warnlimit_oid, "-Oqv", "");
        $limit = snmp_get($device, $limit_oid, "-Oqv", "");
        $lowlimit = snmp_get($device, $lowlimit_oid, "-Oqv", "");
        $warnlowlimit = snmp_get($device, $warnlowlimit_oid, "-Oqv", "");

        discover_sensor($valid['sensor'], 'humidity', $device, $oid, $index, 'akcp', $descr, '1', '1', $lowlimit, $warnlowlimit, $limit, $warnlimit, $humidity);
      }
    }
  }
}

?>